EFP SL48GSTD works with or without an AC ballast to convert new or existing fluorescent fixtures into unobtrusive emergency lighting. They maintain illumination of one lamp or two lamps in the emergency mode for a minimum of 90 minutes.
Emergency fluorescent power pack for fluorescent fixture applications.
When battery packs are remotely mounted, the remote distance cannot exceed 1/2 of the distance from ballast to lamp specified by the A.C. ballast manufacturer. The maximum allowable remote mounting distance is 50 feet.
Low profile galvanized steel construction
Operates one or two T5, T5HO, T8, T12, Circular T5/T9, U-bend T8/T12, 4-Pin CFL and long CFL lamps in emergency mode.